4.0 SHOP DRAWINGS
Two sets of shop drawings including all design calculation and data sheets for construction and/or installation of the whole acoustic treatment for the generator room shall be submitted to the S.O.’s Representative for approval. The Electrical Contractor shall prepare and submit such shop drawings, design calculation sheets and data sheets for the whole work or parts of the work together with their approval from JAS at least two weeks before the work begins. If the shop drawings/documents submitted are not acceptable by the S.O.’s Representative, the Electrical Contractor shall amend and re-submit the shop drawings/documents within two weeks from the date of return of the shop drawings. No work including fabrication of the silencers, acoustic doors and acoustic treatment shall be carried out without the shop drawings being approved by the S.O.’s Representative.
The shop drawings shall include and show the following:
(a) The dimensioned general arrangements, construction layouts of silencers, acoustic doors and all others necessary for the complete acoustic treatment for the generator room/building as specified in the Drawings and/or Bill of Quantities;
(b) The dimensioned general arrangements, layouts, routes and positions of all silencers, acoustic doors and any acoustic treatments in the generator room/building;
(c) The dimensioned layouts and positions of all holes and cut through in the walls and floors for the silencers, acoustic doors and
any acoustic treatments.
The cost of all these shop drawings, whether or not provided in the Bill of Quantities, is deemed to be included in the Contract.