GENERATOR ROOM AND SWITCH ROOM
Whether or not provided in the Bill of Quantities, following safety signage and devices shall be supplied and installed in the generator room and the generator switch room:
(a) One unit. 9 kg dry powder fire distinguisher for A, B,C class of fire complete with pressure gauge, discharge hose with nozzle and
wall bracket, installed on the wall near the door or at the position to be decided by the S.O.’s Representative. The extinguisher shall
be certified by Jabatan Bomba Dan Penyelamat Malaysia valid to be used for a period of twelve months from the completion date of
(b) Approved type of rubber mats shall be provided in front of the switchboards and any other control boards. The rubber mats of
thickness not less than 6 mm and width 1000 mm shall extend to the full length of the switchboards and control boards.
(c) One unit Electric Shock Treatment Chart;
(d) One unit standard notice displaying the words `BAHAYA’ conforming to Electricity Regulations 1994;
(e) One unit standard notice displaying the words `DILARANG MASUK’ conforming to Electricity Regulations 1994;
(f) One unit standard signage `DILARANG MEROKOK’;
(g) One unit 300 mm x 150 mm signage displaying the words `BILIK JANAKUASA’ for generator room;
(h) One unit 300 mm x 150 mm signage displaying the words `BILIK SUIS JANAKUASA’ for generator switch room and
(i) One unit epoxy power coating finish metal writing top with drawer of suitable size shall be provided for keeping the service
and maintenance record book in the generator room. The writing top shall be wall mounted at the position to be decided
by the S.O.’s Representative.
All trenches in the generator room and generator switch room shall be clear from debris and filled up with clean sand to a level above cable ducts. All cable duct entry into the cable trench shall be sealed tight with cement against water and rodent entry.
One set of the following approved as-installed drawings of durable quality shall be framed up in the generator switch room:
(a) Location layout of earthing points with respect to the Generator Room;
(b) Layout and schematic control wiring of the generator set control board; and
(c) Layout and schematic wiring of the generator set switchboard.